الحمد لله والصلاة والسلام على رسول الله وعلى آله وصحبه أجمعين
EQUIPMENT DETAILS Chilled water pumps
SCHEDULE OF PLANNED PREVENTIVE MAINTENANCE Work Plan
Chilled Water Pumps
صيانة دورية جداول جاهزة مضخات الماء البارد
Make & Model
Annual Requirements to Short Life
Consumable Spare Parts
W / Weekly M / Monthly Q / Quarterly SA/ Semi/Annually
A/ Annually SST / Seasonal Start/Up SSH / Season Shut Down
2W M 3M
6M A Notes
Check the operation and abnormal noise/sound
Check gland and mechanical seals for leakage
Check and clean strainer
Check and grease the pump bearing
Check the coupling wear
Check the alignment
Paint if necessary
Change pump packing
Check mechanical seal for leaks, change if
Clean inside pump casing and epoxy coat
Inspect unit for unusual noise and/or vibration, ensure that it is in good working order.
Provide lubrication, if necessary.
If unit is not running or an identified problem requires the unit to be serviced,
perform ALL Non-Critical Tasks listed below.
Flush and clean strainers.
Check operation of gauges and record pressures and temperatures.
Inspect seals and packing, tighten or replace as necessary.
Lubricate impeller shaft bearings.
Inspect motor and pump alignment.
Other recommended tasks
Inspect mounting bolts and vibration isolators of the pump under load conditions.
Start and stop pump, noting any vibration and overall performance.
Inspect drive shaft coupling.
1 Use additional sheets if required
2 PPM routines based on Complete
Running hour where recommended by the Manufacturer
في أمان الله !
148.5 KB Views: 659